South Bay Water Reclamation Plant
One of SBWRP’s final treatment stages is the disinfection of the reclaimed water before distribution. The plant uses an ultraviolet light (UV) system where submerged UV lamps kill or render pathogens unable to multiply. The previous UV disinfection system had been in operation since 2004 and was reaching the end of its useful life. In addition, the City preferred a more energy-efficient system requiring less maintenance.
The City partnered with LEE + RO on the design of a new UV system that not only is more efficient resulting in reduced maintenance time and cost, but also ensures that the reclaimed water is safe and ready for distribution in the future.
The existing Trojan UV4000 disinfection system had been identified by the City to be beyond its useful life and the units no longer met current energy efficiency standards. The objective of this project included evaluation of alternatives to replace the existing UV system with the latest technology available and prepare design documents based on the recommended UV system.
The new UV system required specific manufacturer-supplied electrical equipment used for controlling and powering the UV lamps and, ultimately, the UV disinfection process. Additionally, the new UV system required several ancillary power distribution and protection devices not provided by the manufacturer. The new system was designed and integrated with the existing wastewater treatment facility.
A driving factor for the project schedule was the allowable outage period for the UV disinfection system. With the UV disinfection system out of service during construction, the City is not able to provide reclaimed water to the end users and the City must discharge the effluent to the ocean after secondary treatment. Because the City provides recycled water to several customers, the outage period had to occur during the peak rainy period as demand for recycled water used for irrigation is the lowest during that time.
Another critical item driving the outage period was the time required by the State of California to review the test results and issue the permit to allow the City to once again start supplying recycled water. As most of the project construction took place during the COVID-19 pandemic, that had to be taken into account as well.
San Diego County imports more than 80% of its water. Shutting down the system for an extended period would add additional costs. As most of the construction took place during COVID-19, protocols that were put in place to ensure a safe work environment adversely impacted the delivery of materials as well as the management of the project teams. Additional accommodations had to be made for the subcontractors that were out of state and for the border crossing of the UV system, which was coming from a Canadian supplier.
LEE + RO’s innovative design of the new system allowed the project to have an aggressive construction schedule that not only minimized downtime but took into account the seasonal demand for recycled water.
Energy efficiency was a critical component for this project. LEE + RO conducted a detailed evaluation of alternatives for UV system replacement. The objective was to find the latest, most energy-efficient technology available that fit within the City’s budget. The new UV system:
The existing concrete UV channel had to be structurally modified to accommodate the new UV system, which is smaller than the old UV system in overall dimensions. The system hydraulic grade lines were evaluated for optimum performance and the existing channel sluice gates and motorized weir gate were replaced.
This project is an excellent example of great teamwork.
Everyone came together to overcome all the major obstacles while working around the recent pandemic. The new UV system was installed and brought online within the client’s expected schedule. Although there were minimal disruptions, the implementation of an agreed-upon set of protocols and the use of modern communication platforms – Facetime, Zoom, MS Teams, etc. kept all the stakeholders informed of status and progress.
The selection of a state-of-the-art UV technology for reclaimed water disinfection using the most energy-efficient technology available on the market was the critical part of the project. The new UV system meets the 100 mJ/cm2 MS2 Title 22 State requirements for UV dose and was installed by modifying the existing UV channel. The existing channel was provided with a new motorized weir gate that allowed the system to meet the optimum hydraulic grade lines.
The new system helps the City comply with Title 22 permit requirements in a more efficient manner by providing better dosage monitoring, a more reliable and maintenance-friendly design, faster response to flow changes, and reduction in algae growth.
APWA – SD/Imperial Counties Chapter: 2021 Project of the Year
ASCE - SD Section: 2021 Outstanding Wastewater Treatment Project